It may seem like generators are all you need for your building to maintain power and it may also seem like it is always ready for power outages. As long as generator machines are maintained, there is nothing to worry about in the power outage of your building and infrastructures.
It is important to properly check generator parts before power outage happens through parts checking. If generators undergo this checking often, owners will have to pay less. A generator needs to be tested to assure its capacity to generate electricity when the power goes out. Services that specializes in Emergency Power Supply System (EPSS) maintenance are usually the ones who do these tests. This article is about generator services, specifically test loading which makes up of instructions in using a genset or an artificial load that is useful in measuring the efficiency of the generator. An independent generator service provider is more needed than a generator manufacturer in finding the mentioned services. While manufacturers are more particular on how to improve their product and on the profit they make, EPSS services make use of time to provide testing and maintenance in a very affordable price.
If you think you have to get your generator checked, contact the website of your generator service for an emergency power testing for free, especially if your infrastructure has a level 1 generator.
Load testings are needed to know the efficiency of generators, whether they operate in the nameplate kilowatt ratings. The first step involves a monthly test that is done under National Fire Protection Association (NFPA) code 110 guidelines. The genset must work successfully under existing load and either it operates at least at 30% of its minimum kilowatt rating or achieve the least exhaust gas temperature in order to pass the monthly testing. If not achieved, NFPA 110 imposes that the generator needs to be tested yearly with artificial load that need load bank.
Load bank testing usually increases the efficiency of the generator. Another good thing is that, it can fix wet-stacking – in which the generator’s exhaust side traps unburned fuels. Load banks are successful in evaporating unburned fuels that causes wet-stacking. The unburned fuels need to be evaporated so that parts of the generator will not get broken.
You if want to avail generator services like load testing, independent generator services can conduct anytime. It is better to consult for an emergency power testing before a power outage happens.
Power outages can be avoided by having a generator. Regardless of the kind of generator you have, maximizing its purpose requires you to keep it intact with its parts and checked from time to time.